Compressor thermistor error Compressor Thermistor Error — Compressor temperature thermistor is open or short-circuited while power is on or running the compressor. The number of generations is reset if the start-up of the compressor succeeds. Diagnosis Method Operation Timer Economy. Compressor detection — The compressor speed does not synchronize with the control signal. Heat radiation is blocked. The power supply frequency cannot be recognized after 4 seconds of power on.
|Date Added:||15 June 2004|
|File Size:||54.37 Mb|
|Operating Systems:||Windows NT/2000/XP/2003/2003/7/8/10 MacOS 10/X|
|Price:||Free* [*Free Regsitration Required]|
Outdoor Unit Temperature Error. After the compressor restarts, if the same operation is repeated within 40 seconds, the compressor stops again.
Intake Grille Error — When the micro switch is detected open while running the compressor. If the pressure switch is open for 10 seconds when the power is turned on.
Drivers for AVerMedia USB MPEG-2 Capture Device (E)
Upper air flow -Check operation of limit switch. Check thermistor resistance value. Discharge Thermistor Error — When discharge pipe temperature thermistor open or short-circuit is detected at power on or while running the compressor. AC Rittal error code. Indoor unit fan motor 1 error fujitssu Forced auto switch open pushed in for 30 consecutive seconds or more.
Serial communication error Communication Error — At Start Up, evaporator and condenser are not communicating. The number of generations is reset if the compressor is able to start up. When the compressor becomes hotter than Check DC V on fan. Pressure Sensor Error e8882 Detects after 30 seconds or more after power up when the pressure sensor detection value detects the condition below continuously for 30 seconds or more: Over current error Trip Detection — Protection stop by fuujitsu generation after inverter compressor start processing completed generated consecutively 10 times.
Current sensor error Current Sensor Error — When input current sensor has detected 0A, while the inverter compressor is operating at higher than 56rps, after 1 minute upon starting the compressor.
Halcyon MINI-SPLITS Error Codes
Excessive high pressure protection on cooling mode has been activated. Combination Error — The outdoor unit received a signal that the applied indoor unit is that of a multi type. Suction gas thermistor error Suction Gas Thermistor Error — Suction gas temperature thermistor has shorted or open detected. Compressor Thermistor Error — When the compressor temperature thermistor is open or short-circuit is detected at power up or while running the compressor.
Wired R emo t e Code N o. Communication error- evaporator and wire remote controller are not communicating. Pressure switch error If the pressure switch is open for 10 seconds when the power is turned on. Check for correct voltages at panel, condenser and evaporator. Compressor Thermistor Error — Compressor temperature thermistor is open or short-circuited while power is on or running the compressor.
Check for running compressor with outdoor fan off. Except during defrost operation -Check if terminal connection is loose.
E driver free download for windows – FUJITSU – LifeBook N Series
Wired Remote Controller Communication Error — When the indoor unit cannot receive the signal from the Wired Remote Control for more fujtsu 1 minute during normal operation. Outdoor unit main PCB error Number of Wires and Pipes Error — When the operation command is inputted by the remote controller without check operation completion.
Trip Detection — Protection stop by overcurrent generation after inverter compressor start processing completed generated consecutively 10 times. Outdoor voltage error fujitus Active Filter is detected. Discharge thermistor error Discharge Thermistor Error — When discharge pipe temperature thermistor open or short-circuit is detected at power up or while running the compressor. Check for correct voltage at panel, condenser and evaporator. Outdoor unit fan motor 2 error Outdoor Unit Fan Motor 2 Error — When the outdoor fan rotation speed is less than RPMs in 20 seconds after the fan motor starts, the fan will stop.
After 2 minutes 20 seconds of stopped operation, the signal from the outdoor unit is received even though the main relay is off.